Not feeling heat and noticing error code 228 from your Lennox® furnace?
This indicates your HVAC equipment couldn’t correct its pressure switch before turning on. As a consequence, your system will not run for your protection.
Repairing or replacing this part is best left to the Experts at Stevenson Service Experts Heating & Air Conditioning in Dayton. Our NATE-certified technicians are among the elite in the industry. They’re well-prepared to work on all of your heating needs, including clearing a furnace error.
We want you to be absolutely satisfied with our quality furnace repair in Dayton. That’s why we back it with a 100% Satisfaction Guarantee* for a year.
How a Pressure Switch Works
This part plays a critical duty as your furnace prepares to warm your house.
Here’s what happens after your thermostat’s call for heat:
- Your furnace’s control board commences running the draft inducer blower motor. This exhausts combustion gases from the heat exchanger and moves in new gas and air so the burners can fire.
- When the pressure switch senses that enough air is being pulled into the burners, it closes and commands the control board to ignite the furnace.
- Your furnace ignites and creates heat.
What Happens When a Pressure Switch Malfunctions
When your pressure switch isn’t operating the way it should, you’ll likely hear the fan run and the switch clicking multiple times before the furnace shuts down completely. When a part isn’t performing right, your furnace will turn off for your safety.
Your furnace will let you know something is amiss with a red flash from its indicator light, which it uses to display error codes. It uses this red light to flash code, like Morse code.
You may see short flashes or an alternating slow flash as it communicates a fault code.
Estimated Repair Cost for Furnace Error Code 228
Before replacing the switch, your Stevenson Service Experts Heating & Air Conditioning tech will investigate other parts of your furnace first. Several other issues can also cause the error code, like a clogged vent or cracked hose.
The cost to repair your furnace depends on what’s wrong with it and how long it takes to fix it.
If your pressure switch needs to be replaced, you can plan to pay between $40 to $350.
Count on the Experts at Stevenson Service Experts Heating & Air Conditioning
If you require furnace repair, trust the professionals from Stevenson Service Experts Heating & Air Conditioning to check out the fault code and fix the problem to your satisfaction.
Call us at 937-503-7896 or schedule an appointment online today.